Hello everyone. I put myself to the challenge of installing a CAP (Tri, 10 Kw) with notes of my gas boiler existante.Je stumbles on adjusting the four-way motorized valve , this one is equipped with auxiliary electrical contact which is connected to the central management, but I do not know what it is and what should be the position of the cam which order? The ESBE is graduated from 0 to 10, 0 closed, 5 full opening of the circuit of CAP and 10 full opening of the succession. Thanks for your help
We need the make and type of your PAC and your gas boiler and a brief description of your installation, Second setting commissioning of equipment of this importance should be made by a company certified by the mark of the CAP, it will be able to solve small problems setting you describe. This intervention is essential to obtain warranty and comply with regulations on refrigerants. Regulations require an annual inspection of the sealing equipment containing more than 2 kg of fluorinated refrigerant fluid
Good evening and thank you for your commentaires.Ma first response does not appear I will retry again. For Pat38 if I install it to save on my heating installation but will control the connections and of course the commissioning. This gave me the info for the auxiliary switch, it is positioned at 50% opening of the valve. You soon
To me the comment pat 760 I am fully satisfied he has done everything that has not need for competence partiticuliÃ¨re and left a career doing what is regulated and specialized, some connections, sealing, setting srvices, settings, ect.
In doing so, it will guarantee a functional installation and line